A.1- This specification defines the requirements for Generator Tap Boxes assembled by PSI Control Solutions.
A.2- Generator Tap Boxes provided by PSI Control Solutions shall be completely assembled by a certified ISO
facility. PSI Control Solutions is ISO9001 certified. Number-C0098005-IS1
B.1- The purpose of the Generator Tap Box when installed properly is to provide an easy means to quickly
connect a temporary generator to a site due to utility or other power source failure.
B.2- The Generator Tap Box shall be installed on the building exterior and be hardwired to main switchboard
or transfer switch.
C.1- Generator Tap Boxes shall be completely assembled and undergo a functional test procedure prior to
shipment from PSI Control Solutions. This test shall be documented and included with the Generator Tap Box.
C.2- All Generator Tap Boxes shall be built in accordance with the National Electric Code.
C.3- Generator Tap Boxes that require a UL label shall be built in accordance with UL508A.
D.1- PSI Control Solutions warrants the products manufactured by it and delivered hereunder will be free
from defects in material and workmanship for a period of twelve (12) months after date of shipment.
II Product Requirements
A.1- All components shall be new and free of defects.
B Electrical Ratings
B.1- Generator Tap Boxes shall be rated for single phase 100-240VAC and three phase 208-600VAC.
B.2- Generator Tap Boxes shall be available in an ampacity range of 400-4000A.
B.3- Generator Tap Boxes shall be available in both three and four wire configurations.
C.1- Enclosure shall be NEMA Type 3R, wall-mount with welded mounting tabs or free-standing with mounting feet.
C.2- Enclosure material shall be galvanized steel with RAL7035 light-gray finish or Type 316 stainless-steel.
C.3- Enclosure shall have both a hinged front access door with padlockable wingknob latch, and hinged bottom
access door for cable entry. Bottom access door shall have rubber bumpers to limit range of motion.
C.4- Enclosure shall have two louvered side vents for additional airflow.
C.5- Enclosure shall have a ten gauge interior angled shelf with welded support brackets and cutouts for
C.6- Enclosure shall have removable cover secured with slotted hex head screws.
D.1- Cam-plates shall be ten gauge galvanized steel with RAL7035 light-gray finish or Type 316 stainless-steel.
D.2- Cam-plates shall be interchangeable with hole-cutouts for E1016 Cam-Lok® receptacles.
D.3- For single phase or three-wire applications, a blank cam-plate shall be installed in the empty cutout.
E Cam-Lok® Receptacles
E.1- Cam-Lok® receptacles shall be insulated single pole, Cooper E1016 series, male or female with a single
hole busbar connection.
E.2- Cam-Lok® receptacles shall be color coded for each phase depending upon system voltage.
208-240VAC-Black, Red, Blue
480VAC-Brown, Orange, Yellow
575/600VAC-Black, Black, Black
E.3- Ground Cam-Lok® receptacles shall be bonded to the enclosure.
F.1- Busbar shall be tin-plated copper with mounting holes for mechanical lugs or boltholes for compression
F.2- Busbar shall be sized at 1000A/sq. in.
G.1- Lugs for permanent conductors shall be aluminum, dual rated, with a mechanical screw.
G.2- Lugs shall accept a wire-range of (1) #2-750 MCM.
A.1- The Generator Tap Box shall be installed correctly according to the provided manual and in an appropriate
A.2- Wall-mounted Generator Tap Boxes shall be installed on a building exterior or equivalent.
A.3- Free-standing Generator Tap Boxes shall be installed on a flat, level surface.
A.4- Installation shall be in accordance with all applicable codes and standards
B.1- Enclosure penetrations for cable entry shall be used with appropriate components to maintain the NEMA
C.1- When the Generator Tap Box is properly installed and ready to accept a portable generator, the installer
should follow operational instructions specified in the manual provided.